Case Study: Town Hall Inn
This downtown Toronto 225 all-suite hotel offers an exceptional location, convenient for travellers of business and leisure alike, as well as modern amenities for extended stays. SensorSuite’s SuiteHeat solution is saving this hotel around $23,000 per year with a Return on Investment (ROI) of 2.5 years.
Town Inn Suites applied for the saveONenergy RETROFIT Program, funded by the IESO and received $35,120 as a project incentive. Savings of up to 31% were measured and verified. SensorSuite’s SuiteHeat solution is saving this hotel approximately $23,000 per year with a ROI of 2.5 years.
SensorSuite has been providing free saveONenergy Business program support to Toronto Hydro business customers since 2012. This includes acting as the Applicantion Representative for any business customers seeking incentives for completing electricity saving retrofit projects in collaboration with SensorSuite.
As the Application Representative for Town Inn Suites, SensorSuite looked after the entire incentive application process in an effort to realize the maximum incentive amount available for this Custom Track retrofit project.
As a new SensorSuite client, this service was extended to Town Inn Suites for free.
DOWNLOAD THE CASE STUDY
Rising Energy Costs
Achieve energy bill savings through demand management without affecting customer experience
Remote management of suites and building controls
Enable remote, decentralized load management for scheduling and consumption reduction
SensorSuite Matrix™ Platform
SensorSuite® installed its SensorSuite Matrix™ gateway and 225 EM1 Wireless Energy Management controllers on every PTAC unit in the hotel. Every controller had a temperature sensor, motion sensor, and power sensor. After two initial weeks of gathering baseline data, the controllers were set to function in Demand Management mode. EM1 Energy Management controllers perform demand management intelligently by enabling electrical loads to communicate and coordinate with one another, thereby reducing the number of loads running at the same time. The system’s proprietary SensorSuite Matrix™ platform allowed for significant reductions in electrical demand while maintaining occupant comfort. The controllers also did this automatically, eliminating all intervention from the facility employees.